The lighting pole shall be from thick walled ASTM A48, Class 30, cast iron.
Two (2) access doors in the base and (1) hinged access door in the column (8 7/8” x 7 1/8” minimum opening) shall be secured with stainless steel hardware. A 3/8”-16 UNC grounding lug provision shall be provided inside the base of the pole.
The pole shall be finished with a high performance coating achieved with a three step paint process. An acid etching industrial wash primer, two part epoxy base primer, and a finish coat that is a two-part aliphatic acrylic polyurethane. Paint shall be weather, corrosion, abrasion, and UV resistant in compliance with the Society for Protective Coatings SSPC-36 (level 3) paint standard. Color to be specified.